Where is the pressure relief valve on a combi boiler?
#3 – Check the safety discharge pipe This is called the Pressure Relief Valve Discharge Pipe (or commonly called the ‘P.R.V. ‘) It’s a small pipe, which can only be seen on the outside wall of where the boiler is installed.
What happens if pressure relief valve fails boiler?
Like all components, they can just fail or once triggered often then never quite seal back up, this results in the pressure dropping and an incorrect diagnosis that there is a leak on the heating pipework. In reality, the water is being slowly discharged out from the relief pipe, normally located outside.
How do you relieve pressure from a combi boiler?
How to reduce your boiler pressure
- Switch off your boiler and wait for the heating system to cool.
- Identify and check the boiler pressure gauge.
- If it’s above 2 bars, you’ll need to reduce the pressure.
- Ensure the filling loop or relief valve is tightly closed.
Why does my combi boiler keep losing pressure?
Your combi boiler can be losing pressure for a number of reasons. Pressure loss may be caused from a leak in the pressure relief valve, an issue in the expansion vessel, air in your system, or a leak in the heating pipework itself.
Why does my combi boiler overflow keep dripping?
Your boiler’s overflow pipe may leak water if: The boiler has built up too much pressure due to the expansion vessel failing or losing its charge. The pressure relief valve is not seated correctly, causing water to pass by it.
How do I adjust the pressure relief valve on my boiler?
The lock nut can be loosened if you remove the fast fill lever cap. Slowly turn the adjusting screw clockwise until the system gauge shows the pressure required. The adjusting screw has to be turned counterclockwise to lower the pressure.
Why is the overflow pipe from boiler dripping?
Why does my Worcester Bosch boiler keep losing pressure?
What can cause low boiler pressure? Bear in mind that it’s quite normal for a boiler to slowly lose pressure over time, but a very sudden drop in pressure could indicate a leak somewhere in your system. It can also be caused if you’ve recently bled your radiators.